The Benefits and Challenges of Using NEC Article 392 Pdf for Cable Tray Projects
(B) In Industrial Establishments. Wiring methods of 392.3(A) can be used in accordance with their respective article's requirements. Where only qualified maintenance personnel are available, certain cables are permitted in ladder, ventilated trough, and ventilated channel-type cable trays. Single-conductor cable must be 1/0 AWG or larger and be permitted to be used in cable tray. If the cable is sized 1/0 AWG through 4/0 AWG, it must be installed in ladder-type cable tray with a maximum rung spacing of 9 in. or in ventilated trough cable tray. Welding cable can be installed in accordance with Article 630, Part IV. Equipment grounding single conductors can be insulated, covered, or bare 4 AWG or larger. Multiconductor cable type MV can also be installed as noted above.
Nec Article 392 Pdf Download
PDF .In order to view the full text of these files, you need to obtain a copy of the Adobe Reader for your computer. Click on " Get ADOBE READER " icon to link to a site to download Adobe Reader.
If you are generating a PDF of a journal article or book chapter, please feel free to enter the title and author information. The information you enter here will be stored in the downloaded file to assist you in managing your downloaded PDFs locally.